Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Welcome to the Schneider Electric Global Website×
Can the BMXART0814 module be used without the ABE7CPA412 and maintain use of all 8 channels for Thermocouple operation?
Yes, using a 2-wire PT100 RTD wired to channel 4 on terminals EX+ and EX-. This will allow all 8 channels of the BMXART0814 to be used for thermocouple operation as configured and with one CJC termperature.