Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
Yes. If your NxT project contained PID2 parameters in state ram, they will come over as initial values in Unity. These values will be written to the PLC when you load the program. The parameters should work as is, but in some cases they might require some tuning.
Note: Initial values are only transferred to the PLC if "%MWi reset" or "Initialize %MWi on cold start" is selected in the PLC configuration prior to transferring the project to the PLC.