Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Schneider Electric Global Website×
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
The replacement for the Magelis XBTGT6330 is HMIGTO6310.
No change for cut?out dimensions.
Connection to the Profibus DP, DeviceNet and CanOpen field buses is not possible,
Only RS232 serial link is possible with COM1. Use COM2 with RJ45 connector for RS485 serial.
There is no alarm output or loudspeaker output
SD cards should be used instead of CF cards. (capacity up to 4Gb).