Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
After connecting a VAMP 10L (VAM10LSE) module to a VAMP 321 the error light is illuminated.
The VAMP module must be configured to talk to the VAMP 321. Until this communication connection is established the VAMP 10L module will be in an error status.
Connect to the VAMP 321 using the VAMPset software. Navigate to the ARC Protection screen, then click on the Install arc sensors and I/O units > select install, then write the changes to the VAMP 321. The VAMP 321 will locate all I/O devices along with any connected sensors.
Sign up for all the latest solutions, offers and best practices straight to your inbox.
We are excited that you have joined the group. You will receive your welcome email soon describing the program and what to expect in the upcoming weeks. Enjoy!