Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
When attempting to reset the peak demand from the front panel, the customer may see "Error Demand Lockout" on the display (as shown below).
The "Demand Lockout Time" register within the meter's Display Options Module sets the minimum time allowed between consecutive demand resets; the meter ignores any attempts to reset the demand outside the bounds of the register. The default value for the Demand Lockout time is 25 days.
The customer can open the Setup Assistant for the meter in ION Setup. Then, click on Demand--> Rolling Block tab and configure the Demand Lockout. By default the "Demand Lockout" is set to 25 days. If the customer would like to reset the demand from front panel more often they should decrease the number of days.
An alternate way to reset the peak demand is to connect to the meter using ION Setup and navigate to the data screen view. View --> Data Screens --> Demand.
Click on the button for Peak Demand Reset.
Sign up for all the latest solutions, offers and best practices straight to your inbox.
We are excited that you have joined the group. You will receive your welcome email soon describing the program and what to expect in the upcoming weeks. Enjoy!