Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
Using the "Parameter" screens the module is configured for its set points,max value
and mode of operation. To reset the count is a simple matter of sending a command
to the first 4x register of the module's I/O map reference. Prior to doing anything you
should be aware of the terminology involving this module.
Reset: Turning off the output coils associated with the card. Reset has nothing to do
with your count values being set to 0 or max value.
Preset: This can be a hardware input or software command. Preset will set your current
count to zero if your counting up, or to max value if your counting down.
To perform the initial start up of the module you can send any of the following commands
based upon the number of counters being used. The value should be sent to the 1st
4xxxxx or %MW assigned to the module in the IO Map.
To Preset and Enable counters 1 and 2... Send the value 233H to the module.
To Preset and Enable counter 1 only......... Send the value 203H
To Preset and Enable counter 2 only..........Send the value 230H
Following the Preset and Enable command you will send the Read command to the 1st
4xxxxx or %MW reference assigned to the module in the IO Map
Read Counters 1 & 2 ...............................Send the value 300H
Once the PLC application is running and you wish to Preset and Enable counters 1 & 2
send the following commands to the EHC202.
To Preset and Enable counters 1 and 2... Send the value 0033H to the module.
To Preset and Enable counter 1 only......... Send the value 0003H
To Preset and Enable counter 2 only..........Send the value 0030H
If you want to know what the last count was prior to Preset send a 400H command. This command
will buffer the last count seen by the counters just before the Preset command arrived.
Remember, you can Preset the module with hard wired inputs to the Preset input of each counter or
you can use the software Preset described here. A hardware Preset is accomplished by pulsing the
Preset input terminal on the EHC 202 for counter 1or counter 2. It is permissible to use both methods
simultaneouslyif you wish. Follow the wiring diagrams in the Quantum Hardware Reference Guide
they are accurate and should be relied upon for proper module operation.
Sign up for all the latest solutions, offers and best practices straight to your inbox.
We are excited that you have joined the group. You will receive your welcome email soon describing the program and what to expect in the upcoming weeks. Enjoy!