Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Welcome to the Schneider Electric Global Website×
7500 ; 7600 ; 7550 ; 7650 ; ION Setup ; MV90 ; MV-90 ; MV 90 ; Report ; Template
The setup assistant window of an ION 75x0/76x0 meter doesn't include MV90 reports by default. To add the MV90 report, the template of the meters needs to be modified.
Log into ION Setup in Network mode and view the device properties by right-clicking on the meter icon in the network viewer then bring up the Display Tab.
Now Go to Program Files\Schneider Electric\ION Setup\Tables and open the folder specified in template type.
In this folder, open the folder specified under template options and open the "QuickIon.cfg" with the notepad.
The "Report" section is all the way down to the bottom. Copy and paste these two lines at the end of the file:
Tab1Reg7Text=This reports information useful for MV-90 and allows saving info to a MV-90 Master file for importing.
Then modify the line "Tab1Registers=6" to "Tab1Registers=7" as a seventh report was added.
Save and Close the QuickIon.cfg file.
The MV-90 report will now be available in ION Setup.
All content © 1992-2007 Schneider Electric