Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Welcome to the Schneider Electric Global Website×
External boolean module, external numeric module and external pulse module do not have any input registers and ION Reference tells that these modules are controlled via communication.
To activate/deactivate these modules through ION Setup, we need to first open the module in ION Setups advanced mode, select the output register tab and
2. For external numeric module, hold down the shift key on the computer key board and single left click the numeric register (there are two output registers; one is numeric register and the other one is event register) to input desired number.
3. For external pulse module, hold down the shift key on the computer key board and single left click the trigger register (there are two output registers; one is trigger register and the other one is event register) to send a trigger.