Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
Goals and Symptoms
When running a report in information manager for the virtual circuit node the KWH value is higher than running the same report with the physical devices together.
Causes and Fixes
This happens when there is not a KW rating set for the physical device.
1. In the SMS Setup Utility open system to configure.
2. Go to Setup> Device\Routing, select a meter that pertains to a virtual circuit node, and click Ratings