Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
It is possible that the frequency reading on a Series 2000 Circuit Monitor (CM2000) will read 32,767 when all other readings are correct. This is typically caused when the nominal frequency setting in the meter does not match that of the actual system being metered. Example: The system being metered is a 400HZ system but the meter nominal frequency setting is still set at the default of 60HZ.
Date Created: 5 Aug 2007
Original Author: RM
Last Revised: 5 August 2007
All content © 1992-2007 Schneider Electric