Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Don’t miss the latest events, videos, or articles. It’s all in our news bulletin.Sign up now
Schneider Electric Global Website×
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
From the source code of the firmware for 37xx meters, the meter will suppress relays, setpoints, and alarms for 3 seconds during power up. In other words, relay outputs will be inhibited until the 3 second initialization period is over after a power up. There is no way to change these values since it is coded into the firmware.