The Internet of Things (IIoT) offers unprecedented possibilities for industries. Stay ahead with EcoStruxure™ Plant and Machine.Learn more
...with the EcoStruxure™ Facility Expert (formerly known as Facility Hero) app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
The story behind the Shedd Aquarium, a smart, sustainable facility that connects people to animals, with EcoStruxure™.Discover how
Welcome to the Schneider Electric Global Website×
The output registers of a Modbus Master Device Module contain the imported Modbus data for other ION modules to use. The output labels are derived from other registers as shown below:
<label><bit number>@<slave name>[value]
The label is acquired from the Modbus Master Map modules Device Map register (The bit number applies to Packed Boolean formats only).
ION Enterprise has a known issue with the use of @ symbol in OPC registers, which by default exists in the outputs of the Modbus Master Device Module. Hence, these registers cannot be made available for OPC directly from the Modbus Master Device Module. An alternative solution can be the use of a "dummy" arithmetic module in the meter or the VIP.
Sign up for all the latest solutions, offers and best practices straight to your inbox.
We are excited that you have joined the group. You will receive your welcome email soon describing the program and what to expect in the upcoming weeks. Enjoy!