Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Welcome to the Schneider Electric Global Website×
The ION6200 can measure V L-L Avg as well as V L-N Avg, however in delta mode, since there is no neutral, V L-N Avg is not available. What is shown on the front panel display is V L-L Avg and it is labeled V Avg. The meter's firmware is designed to display this quantity on the front panel. Having said that, V L-N Avg is available through Modbus or ION protocol with any ION software.