Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
Blank meter name
Run-time error 1004
The error message that appears will look like the following:
There are a couple solutions to this issue.
Method 1) Create a new device with a shorter name and use http://www.powerlogic.com/kbarticle.cfm?myrequest=RESL189159 to assign the old data to the new meter.
Method 2) Enable the query-based workflow by unhiding the Template worksheet and setting USEDEFAULTCONFIGVIEW to 0. Next, choose the logs to query, and the name chosen for the query will become the worksheet name. To do this do the following:
a) Browse to ...IONEnterprise\config\reports and open the report in question.
b) Go to Format > Sheet > Unhide
c) Make sure that the USEDEFAULTCONFIGVIEW is set to 0.
d) Save, exit, and try the report again.