Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Welcome to the Schneider Electric Global Website×
Goals and Symptoms
ION Setup v2.2
This resolution shows the procedure to generate a Master file for MV-90 by using ION Setup and shows how to import this Master file into MV-90.
It is not easy to build a Master file on MV-90 manually. ION Setup can help generate a Master file by extracting data from an ION meter and save the edited work in MV-90. However, an improper setting may cause the Master file stop working with MV-90. Some critical steps and settings are shown in this document to make sure the Master file works correctly.
Facts and Changes
Causes and Fixes
Generate a Master File using ION Setup:
1. Install ION Setup v2.2 or later
2. Open ION Setup > Connect to a device > Open Setup Assistant > Go to Reports > Open the MV-90 Report
b. Device ID > Select Tag2 Field/Serial number (for meter identification purpose)
c. MV-90 calls in on > Select the meter com port which works with MV90
d. Connection Info > Input the phone number or IP address+port number
e. Tim Number > 01 (make sure that the assigned number for TIM_ION in MV90 is 01)
f. Click OK
Import master file into MV-90:
8. Switch to the xi COMM window to see the progress of the task.
9. To view the retrieved data, see http://www.powerlogic.com/kbarticle.cfm?myrequest=RESL192306.
(Removed Image URL: /PubResEXPORT.nsf/2b87ee90be777fc085257c28006ee4ef/8ccb5988956e9cbfc125755d001627aa/fl_block_5/0.3070?OpenElement&FieldElemFormat=gif)
Date Created: January 20, 2009
Last Revised: February 13, 2009
Original Author: TL
All content © 1992-2009 Schneider Electric