Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Welcome to the Schneider Electric Global Website×
The user receives a "Negative Acknowledge" message when attempting to read registers through the EGX100 Read Device Registers webpage. This occurs when reading registers from devices connected that use PowerLogic protocol. These devices include Series 100, 200, 2000 Circuit Monitors (CM2000, CM100, CM200), Series 600 Power Meters (PM600), Digital Relays (DR), and PowerLogic Interfaces (PIF3 and PIF85).
This is a list of possible causes but are not limited:
- attempting to read a register which does not exist in a particular device
- incorrectly configured dipswitch biasing on the EGX100 RS485 port
Check to see that the correct register is being read and that the dipswitches are configured according to the diagram above.