The Internet of Things (IIoT) offers unprecedented possibilities for industries. Stay ahead with EcoStruxure™ Plant and Machine.Learn more
...with the EcoStruxure™ Facility Expert (formerly known as Facility Hero) app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
The story behind the Shedd Aquarium, a smart, sustainable facility that connects people to animals, with EcoStruxure™.Discover how
Welcome to the Schneider Electric Global Website×
Goals and Symptoms
ION Enterprise PC was moved from "meter hub" to docking station. After reconnecting to the local area network (DHCP based). After re-opening Designer, a device communication error is received.
Causes and Fixes
Changing the Networking Preferences on an ION Enterprise server without re-booting, or completely restarting ION Enterprise can leave the site communication server in a state of confusion, where it is trying to use the old networking preferences. Testing using ION Setup to try to connect to the meter works just fine. Under this circumstance, a re-initialization of the ION Enterprise services is most likely all that is required. To do this:
After this, Test communications in ION Designer & ION Vista. If communications to the meter have been lost for a substantial period, ION Log Inserter communications (i.e. uploading meter logs) may be heavy displacing ION Designr and ION Vista communications for some time. If this is an issue, you may want to disable the ION Log Inserter service temporarily to enable other communications to occur.
Key words and phrases:
Last Revised: 31 May 2008
Applies To: ION Enterprise
Original Author: LS
All content © 1992-2008 Schneider Electric
Sign up for all the latest solutions, offers and best practices straight to your inbox.
We are excited that you have joined the group. You will receive your welcome email soon describing the program and what to expect in the upcoming weeks. Enjoy!