The Internet of Things (IIoT) offers unprecedented possibilities for industries. Stay ahead with EcoStruxure™ Plant and Machine.Learn more
...with the EcoStruxure™ Facility Expert (formerly known as Facility Hero) app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
The story behind the Shedd Aquarium, a smart, sustainable facility that connects people to animals, with EcoStruxure™.Discover how
Welcome to the Schneider Electric Global Website×
In System Manager Software (SMS) go to Setup > Devices/Routing, click to configure the device that is receiving the input pulses. Click on the I/O Setup tab. Click the Input Metering (IM) Setup button. In the 'Demand Mode For All Channels' box at the top of this window, make sure that the Method is set appropriately. If Method is set to Input Synchronized Block or Input Synchronized Rolling Block, Present Demand (and Last Demand) will not be calculated on the Input Metering channels. These input sync methods tell the meter that the pulse is meant as a sync pulse for the meters calculated Demand and not intended to relay an IM Present Demand value.
Sign up for all the latest solutions, offers and best practices straight to your inbox.
We are excited that you have joined the group. You will receive your welcome email soon describing the program and what to expect in the upcoming weeks. Enjoy!