Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
In System Manager Software (SMS) go to Setup > Devices/Routing, click to configure the device that is receiving the input pulses. Click on the I/O Setup tab. Click the Input Metering (IM) Setup button. In the 'Demand Mode For All Channels' box at the top of this window, make sure that the Method is set appropriately. If Method is set to Input Synchronized Block or Input Synchronized Rolling Block, Present Demand (and Last Demand) will not be calculated on the Input Metering channels. These input sync methods tell the meter that the pulse is meant as a sync pulse for the meters calculated Demand and not intended to relay an IM Present Demand value.
Sign up for all the latest solutions, offers and best practices straight to your inbox.
We are excited that you have joined the group. You will receive your welcome email soon describing the program and what to expect in the upcoming weeks. Enjoy!