Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Welcome to the Schneider Electric Global Website×
One solution is to configure the device for a system type 40 (3-phase 4-wire with 3 CTs). Then wire in all three voltage phases and connect the neutral. Then wire the two current phases (CT) to the corresponding current input. The third phase current input will not have a current transformer (CT) connected. More detail should be discussed with your technical support representative before assuming that the above solution covers each scenario.
The phase current will read 0 for the phase that does not have the CT connected.
The individual KW and total KW will be correct.
All total values will be correct like Energy, power, Kvars, and etc.
Only 3 phase average Voltage will be correct. All other average readings can not be used because 0 will be part of the average value.
There will be a current imbalance since one phase will have zero current.
This applies to the Series 2000, 3000, 4000 Circuit Monitors (CM2000, CM3000, CM4000) and the Series 200, 600, 700, 800 Power Meters (PM200, PM600, PM700, PM800)