The Internet of Things (IIoT) offers unprecedented possibilities for industries. Stay ahead with EcoStruxure™ Plant and Machine.Learn more
...with the EcoStruxure™ Facility Expert (formerly known as Facility Hero) app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
The story behind the Shedd Aquarium, a smart, sustainable facility that connects people to animals, with EcoStruxure™.Discover how
Welcome to the Schneider Electric Global Website×
Do all of the split-core current transformers (CTs) have to be installed on a Branch Circuit Power Monitor (BCPMSC)?
For the BCM and BCPM devices, the CTs are connected to daughter boards that get connected via ribbon cable to the main circuit board. In either case, all of the split-core CTs do not have to be installed, it is sufficient to install just the ones that have a circuit to monitor. If a BCPM or BCM is ordered with 12 CT's and later there is a need to monitor 30 circuits, then only the additional CTs need to be purchased and added.
Note that the CT's initially purchased with the BCPM or BCM are the CTs the main circuit board are calibrated for, and are the only CT's that will meet the given accuracy specifications when measured by the BCPM or BCM.
Sign up for all the latest solutions, offers and best practices straight to your inbox.
We are excited that you have joined the group. You will receive your welcome email soon describing the program and what to expect in the upcoming weeks. Enjoy!