Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Welcome to the Schneider Electric Global Website×
System Manager Software (SMS) v4.2 and lower cannot be used to change remote settings in the Sepam Series 20, 40, and 80 relay. It can only be used to view and log real-time data, capture waveforms, and send TC commands (such as "open", "close", "reset", etc.....) to the Sepam relay.
The SFT2841 software is the software tool used to change settings and operations for Sepam Series 20, Series 40, and Series 80. SFT2841 can be used to load, unload, modify Sepam protection and parameter settings. It can also be used to obtain measurements, and extract useful information during commissioning.
SFT2841 can connect to Sepam devices remotely when they are connected to a to E-LAN multipoint communication network. This network will allow the user to communicate in 4 different protocols: Modbus, IEC103, DNP3 and IEC61850. SFT2841 is also capable of communicating to the Sepam Relay over ethernet using a gateway, such as an EGX.