Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
The default Energy & Demand report in ION Enterprise 3.0 and 4.0 does not rollover for kVARh and kVAh. The rollover occurs properly for kWh.
When a rollover occurs for either the kVARh or kVAh parameter, the report will indicate a negative number or a significantly smaller number than expected for that parameter for the given date range. You should never have a negative energy value in the report unless the integrator module was reset by the user within the given date range.
A discrepancy was found where the kVARh and kVAh labels used in the rollover code of the report were incorrect.
By default, the Integrator module has a rollover value of 10 000 000. The rollover component of the code will not be accurate if the Integrator module has a rollover value below 10 000.
The default Energy & Demand report in ION Enterprise 4.5 or higher will have the required rollover fix. This newer template can be used to replace the existing template in ION Enterprise.
Original article#9722 (SWKB-0358), #9736 (SWKB-0407)
All content © 1992-2007 Schneider Electric
Sign up for all the latest solutions, offers and best practices straight to your inbox.
We are excited that you have joined the group. You will receive your welcome email soon describing the program and what to expect in the upcoming weeks. Enjoy!