Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Don’t miss the latest events, videos, or articles. It’s all in our news bulletin.Sign up now
Schneider Electric Global Website×
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
Goals and Symptoms
The drawing works fine in the System Manager Software (SMS) Setup Utility v 4.0 but the background is missing when viewed through the Web client (Value Blocks, Background Colors, Function Blocks, etc. are visible).
Facts and Changes
Typically GFX diagrams use a background that is a Windows Meta file (.wmf).
Causes and Fixes
The version of the .wmf file used for the background could be an older version that is not being interpreted correctly. Use Visio to open and re-save the .wmf file.
(Removed Image URL: /PubResEXPORT.nsf/2b87ee90be777fc085257c28006ee4ef/32e7f2a974e8e7e3c125734d00160676/fl_block_5/0.1AD6?OpenElement&FieldElemFormat=gif)
Last Revised: August 2, 2007
All content © 1992-2007 Schneider Electric