The Internet of Things (IIoT) offers unprecedented possibilities for industries. Stay ahead with EcoStruxure™ Plant and Machine.Learn more
...with the EcoStruxure™ Facility Expert (formerly known as Facility Hero) app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
The story behind the Shedd Aquarium, a smart, sustainable facility that connects people to animals, with EcoStruxure™.Discover how
Welcome to the Schneider Electric Global Website×
Goals and Symptoms
VIP Not Getting New Data From ION Devices
Data from the VIP appears to be wrong.
In Designer you can see the values on the inputs of a VIP module but the VIP Module doesn't seem to be processing that same data. For example, an arithmetic module might try to add two values from a meter. In designer you can see the inputs to this module as, say, 23 and 54. The formula is to add these two values. But the output of the module remains at 0.
Causes and Fixes
The VIP is holding stale data.
When you look at the values of the inputs in Designer the system is actually going to the meter with a high priority one-shot program to retrieve the values. You are not seeing what the VIP is seeing in its inputs.
Meanwhile the VIP is doing its regular polling of all ION Devices it needs data for. And this polling is competing with all of the other ION clients (e.g VISTA, LogSrv etc).
To validate this problem, create a Data Monitor module in the VIP and point it at the ION Device. Let it run and then check the update period. This will tell you how long it takes for the VIP to see new data.
By default the VIP polls at a LOW priority. You can try to reset this priority higher, say to MEDIUM, but remember that this means that other clients will now not get updates as quickly.
The overall bottleneck is access to the serial communication port. Close VISTA diagrams that look at devices on the constricted port. Disable unneeded Data Recorders on ION devices on this port. This means the LogSrv doesn't have to upload unneeded logs.
As an alternate application, use the VIP as a concentrator. Let the VIP bring in the values of interest for its internal calculations and then reconstruct the Vista diagrams to get the values from the VIP. Vista would not contend for the port.
All content © 1992-2007 Schneider Electric
Sign up for all the latest solutions, offers and best practices straight to your inbox.
We are excited that you have joined the group. You will receive your welcome email soon describing the program and what to expect in the upcoming weeks. Enjoy!