The Internet of Things (IIoT) offers unprecedented possibilities for industries. Stay ahead with EcoStruxure™ Plant and Machine.Learn more
...with the EcoStruxure™ Facility Expert (formerly known as Facility Hero) app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
The story behind the Shedd Aquarium, a smart, sustainable facility that connects people to animals, with EcoStruxure™.Discover how
Welcome to the Schneider Electric Global Website×
Goals and Symptoms
VIP Sliding Window Demand
The SWinDemand output register of the VIP Sliding Window Demand module is incorrect. Instead of averaging the samples over the sub interval, the output value simply reflects the input value at the time the sub interval expires and the output is updated. This can be most clearly seen if only a single sub interval is used.
This problem has existed ever since the VIP Sliding Window Demand module was introduced for Pegasys 2.1.
Facts and Changes
There is no workaround for this problem.
Causes and Fixes
This issue will be resolved for ION Enterprise 5.5 Service Pack 1.
Document Change History
|Date and Initials||Comments|
|2009-10-27 DRM||* Corrected incorrect association to "protection relay PRODUCTS\VIP"
* Re-published to Public security level
All content © 1992-2007 Schneider Electric
Sign up for all the latest solutions, offers and best practices straight to your inbox.
We are excited that you have joined the group. You will receive your welcome email soon describing the program and what to expect in the upcoming weeks. Enjoy!