Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Welcome to the Schneider Electric Global Website×
Goals and Symptoms
VIP Sliding Window Demand
The SWinDemand output register of the VIP Sliding Window Demand module is incorrect. Instead of averaging the samples over the sub interval, the output value simply reflects the input value at the time the sub interval expires and the output is updated. This can be most clearly seen if only a single sub interval is used.
This problem has existed ever since the VIP Sliding Window Demand module was introduced for Pegasys 2.1.
Facts and Changes
There is no workaround for this problem.
Causes and Fixes
This issue will be resolved for ION Enterprise 5.5 Service Pack 1.
Document Change History
|Date and Initials||Comments|
|2009-10-27 DRM||* Corrected incorrect association to "protection relay PRODUCTS\VIP"
* Re-published to Public security level
All content © 1992-2007 Schneider Electric