Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Schneider Electric Global Website×
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
Arithmetic module is outputting N/A for value and causing other calculations to show N/A.
ION Enterprise 6.x, Struxureware Power Monitoring 7.x (SPM) , Power Monitoring Expert 7.2.x (PME)
Arithmetic module output and calculations.
When the Arithmetic module has at least one N/A input, its output equals N/A. In other words, when the Arithmetic module has available inputs and N/A inputs, the other ION modules cannot simply ignore the N/A inputs and only utilize the available inputs.
To convert the N/A to zero, you may use the Convert module. Run the N/A signal through a Convert module and configure the 'N/A convert' register to convert to 0.
Feed the output of the Convert module to the Arithmetic module.
If you cannot predict which signal would be N/A, run each of them through a Convert module and set the 'N/A convert' register to convert to 0.