The Internet of Things (IIoT) offers unprecedented possibilities for industries. Stay ahead with EcoStruxure™ Plant and Machine.Learn more
...with the EcoStruxure™ Facility Expert (formerly known as Facility Hero) app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
The story behind the Shedd Aquarium, a smart, sustainable facility that connects people to animals, with EcoStruxure™.Discover how
Welcome to the Schneider Electric Global Website×
Goals and Symptoms
Web Designer application does not work after updating the Unity application.
Facts and Changes
TSXWMY100, 140NWM10000, BMXNOE0110
Causes and Fixes
The Web Designer application in the module does not work correctly after a change
in the Unity application is downloaded to the PLC.
The reason why the issue occurs is because the signature of the Unity application that was used to
create the 'Variables' table for the PLC service in the 'Factroycast HM'I application, does not match the
signature of the Unity application in the PLC. Whenever a logic or configuration change is made to the
Unity application in the PLC, the signature also changes.
When Unity symbol file is imported into a Web Designer application, the file signature is saved in the
'Factorycast HMI' application. The signature gets transferred to the module as part of the application.
If the signature in the module does not match with the Unity application in the PLC, the 'Factorycast HMI/
Web Designer' services may not function correctly.
To resolve the issue:
Sign up for all the latest solutions, offers and best practices straight to your inbox.
We are excited that you have joined the group. You will receive your welcome email soon describing the program and what to expect in the upcoming weeks. Enjoy!