Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
Goals and Symptoms
OTB export sets the default for the Analog Input Global Interrupt Enable to 1 instead of 0.
Facts and Changes
Advantys version 4.0
Causes and Fixes
CAN OPEN specification 'CIA 401 section 8.5.4 Analog Input Global Interrupt Enable (6423h)'
'This object shall enable and disable globally the interrupt behaviour without changing the
interrupt mask. By default, no analogue input activates an interrupt.'
The exported .eds file from the Advantys Configuration Software version 4.0 incorrectly shows the analog
input as being activated by default.
ParameterName=Analog Input Global Interrupt Enable
As a workaround, you can edit the '.eds' file with 'Notepad' using the following steps.:
Sign up for all the latest solutions, offers and best practices straight to your inbox.
We are excited that you have joined the group. You will receive your welcome email soon describing the program and what to expect in the upcoming weeks. Enjoy!