Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
The purpose of this resolution is to inform Momentum M1E users that the IEC Exec. has been upgraded to version 1.23.
Goals and Symptoms
Resolves an issue with reconnecting from an M1E client to a server using I/O scanner if the M1E is power cycled. The M1E will now reconnect with a different port number. Resolves a reconnect issue when the gateway is powered down.
Facts and Changes
This resolution affects 171CCC98030 and 171CCC96030 processors using the IEC Exec.
Causes and Fixes
Installing IEC Exec. v.1.23 resolves the above mentioned issues