Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Welcome to the Schneider Electric Global Website×
The Reclaim time ranges from 0.1 seconds to 300 seconds. The reclaim time is a timer activated after a closing command is given causing the recloser to sends a tripping command if a fault is detected before the end of the time delay.
The Blocking time ranges from 0.1 seconds to 60 seconds. The blocking time is a timer activated when a condition such as "recloser out of service", "breaker failure", etc... is detected causing the recloser to block the recloser protection function until the end of the time delay.
The Dead time ranges from 0.1 seconds to 300 seconds. The dead time is a timer activated following instantaneous or time-delayed tripping by the protection unit and sends a closing command after the end of the time delay.