Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
For the display ("black" port) we use a standard CAN protocol and for the communication ("green" port) we use a "built in" protocol. These ports are not Modbus protocol.
The CAN protocol does include control power and will supply power to all remote modules (DSM303, MET148 & MSA141). These modules are connected using a CCA77x cable and can be daisy chained by connecting the Dd port (outgoing) to the next module. This will allow control power to be distributed to all modules on the daisy chain. A maximum of 3 modules are allowed on each daisy chain.
The communications protocol does not include control power and it must be supplied separately by a 12V or 24V DC source, as pictured below: