The Internet of Things (IIoT) offers unprecedented possibilities for industries. Stay ahead with EcoStruxure™ Plant and Machine.Learn more
...with the EcoStruxure™ Facility Expert (formerly known as Facility Hero) app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
The story behind the Shedd Aquarium, a smart, sustainable facility that connects people to animals, with EcoStruxure™.Discover how
Welcome to the Schneider Electric Global Website×
A synchronization clock sends pulses to input I21 (series 20, 40)
and input I103 (series 80) every 10 to 60 seconds.
This external clock must be operational before Sepam relay.
The synchronization function takes effect following a time-set.
The relay learns the interval based on the rising edges of the first two received pulses at a logical input (I21).
Thereafter, resetting is based on the measurement of the difference between the relay internal clock and the logical input pulse.
Sign up for all the latest solutions, offers and best practices straight to your inbox.
We are excited that you have joined the group. You will receive your welcome email soon describing the program and what to expect in the upcoming weeks. Enjoy!