The Internet of Things (IIoT) offers unprecedented possibilities for industries. Stay ahead with EcoStruxure™ Plant and Machine.Learn more
...with the EcoStruxure™ Facility Expert (formerly known as Facility Hero) app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
The story behind the Shedd Aquarium, a smart, sustainable facility that connects people to animals, with EcoStruxure™.Discover how
Welcome to the Schneider Electric Global Website×
A current transformer (1A or 5A) is attached to the rear panel of a Sepam relay via the CCA634 connector. The CCA634 connector can connect three (3) phase current transformers and one (1) zero sequence current transformer to a Sepam relay.
The CCA634 connector contains interposing ring current transformers (CT) with through primaries. When measuring phase and zero sequence
currents, these primaries provide impedance matching and isolation between the 1A or 5A circuits and the Sepam relay.
The connector can be disconnected while powered on since disconnection does not open the CT secondary circuit.
Sign up for all the latest solutions, offers and best practices straight to your inbox.
We are excited that you have joined the group. You will receive your welcome email soon describing the program and what to expect in the upcoming weeks. Enjoy!