Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
The MSA141 module converts one of the Sepam measurements into an analog signal. Measurement selection is determined by parameter setting:
0-10 mA, 4-20 mA, or 0-20 mA analog signal according to parameter setting.
To scale the analog signal, set minimum and maximum values of the converted measurement.
Examplethe setting used to set phase current (Ia) as a 0-10 mA analog output with a dynamic range of 0-300 A is: minimum value = 0 maximum value = 300 (3000 .. 0.1A = 300.0 A)
Any one of the CCA770 (2 ft or 0.6 m), CCA772 (6.6 ft or 2 m) or CCA774 cables (13.1 ft or 4 m) connects a single module for each Sepam base unit.
Sign up for all the latest solutions, offers and best practices straight to your inbox.
We are excited that you have joined the group. You will receive your welcome email soon describing the program and what to expect in the upcoming weeks. Enjoy!