Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Welcome to the Schneider Electric Global Website×
The MSA141 module converts one of the Sepam measurements into an analog signal. Measurement selection is determined by parameter setting:
0-10 mA, 4-20 mA, or 0-20 mA analog signal according to parameter setting.
To scale the analog signal, set minimum and maximum values of the converted measurement.
Examplethe setting used to set phase current (Ia) as a 0-10 mA analog output with a dynamic range of 0-300 A is: minimum value = 0 maximum value = 300 (3000 .. 0.1A = 300.0 A)
Any one of the CCA770 (2 ft or 0.6 m), CCA772 (6.6 ft or 2 m) or CCA774 cables (13.1 ft or 4 m) connects a single module for each Sepam base unit.