Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
Using MBMaster to verify that a Modbus device is working.
MbMaster can be used to determine if a modbus device is working.
Run this program from a DOS prompt.
For example here is a sample where I connect to a 6200 device at 19,200 baud. I am using the PC's COM2. The meter's Unit ID is 100 and it is configured to use the Modbus protocol. I am asking for Modbus address 44000 which provides the password for this meter. My meter's password is 0.
MBMaster provides quite a bit of diagnostic information which you can ignore in this case. Just look for the data from the register.
-=-=-=-=-=- Sample MBMaster -=-=-=-=-=-=-=-
H:\\Bin>mbmasterV21M3 -COM2 -B19200 -ID100 -SR44000 -NR1
MBMASTER v2.1M3: Compiled at Jul 13 2001 04:13:57
Stripped BAUD from input: 19200
Stripped SR from input: 44000
About to open ModPL with port COM2
Building request: modslave = 100
Modbus AL frame received: fc = 03
Modbus AL frame: startreg = 404000, #regs = 1
Register 404000: 0
-=-=-=-=-=- End Sample MBMaster -=-=-=-=-=-=-=-
All content © 1992-2007 Schneider Electric