The Internet of Things (IIoT) offers unprecedented possibilities for industries. Stay ahead with EcoStruxure™ Plant and Machine.Learn more
...with the EcoStruxure™ Facility Expert (formerly known as Facility Hero) app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
The story behind the Shedd Aquarium, a smart, sustainable facility that connects people to animals, with EcoStruxure™.Discover how
Welcome to the Schneider Electric Global Website×
Unable to power cycle the meter physically. Need to do remotely or perform soft reset by writing modbus register to the meter.
CM3000/4000, PM8 series
Sometimes local access to where the meters are installed isn't possible or access to the wiring of the meter is blocked.
In this case, remotely write modbus register to meter in order to power cycle the meter. Using software like Tester (software the read/write register):
Write 9020 to register 8000
Then, write 1110 to register 8000
This will reset the meter.
In addition, the PM8 series meter you can write modbus register from front panel. Also, if user has CM3000/4000 with display, they can also write modbus register from front display.
Sign up for all the latest solutions, offers and best practices straight to your inbox.
We are excited that you have joined the group. You will receive your welcome email soon describing the program and what to expect in the upcoming weeks. Enjoy!