Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Welcome to the Schneider Electric Global Website×
Unable to power cycle the meter physically. Need to do remotely or perform soft reset by writing modbus register to the meter.
CM3000/4000, PM8 series
Sometimes local access to where the meters are installed isn't possible or access to the wiring of the meter is blocked.
In this case, remotely write modbus register to meter in order to power cycle the meter. Using software like Tester (software the read/write register):
Write 9020 to register 8000
Then, write 1110 to register 8000
This will reset the meter.
In addition, the PM8 series meter you can write modbus register from front panel. Also, if user has CM3000/4000 with display, they can also write modbus register from front display.