Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
Setting up the CM2000 (Front Panel)
Front panel setup
The following procedure describes how to setup the CM2000 series meter from the front panel.
The following video depicts the process of accessing the meter setup mode and modifying the CT/PT ratios and communications settings.
Press the Mode button to change the Mode to Setup.
When Config appears on the display, press the PHASE [Enter] button.
When P ---- appears, enter the password by pressing the blue arrows.
By default, the password is 0000.
Press PHASE [Enter] button.
The meter is now in setup mode, and the red LED next to AMMETER (A) [CT Primary] will blink.
Press the PHASE [Enter] button to select a configuration item. The red LED next to the selected configuration item will blink.
Press the SELECT METER [Value] buttons to increase or decrease the displayed value until the desired value is displayed.
Repeat steps 5 and 6 until all desired configuration changes have been made.
When all desired changes have been made, press the MODE button once.
The red LED next to K-FACTOR [Accept] will blink. The circuit monitor display will read NO, and the red LEDs next to the changed items will be lit.
Accept or reject the changes.
To reject the changes, press the PHASE [Enter] button once.
To accept the changes, press the SELECT METER [Value] button to change from NO to YES, then press the PHASE [Enter] button. The circuit monitor will go through its restart procedure, indicating that the changes were made.
For more information on the configuration items, see Chapter 5 of the CM2000 Installation and Operation Manual.
Note: The circuit monitor requires that the current transformers (CT) have a 5 amp secondary and the
voltage transformers (PT) have a 120 volt secondary. The primary current and voltage transformer
ratings are entered into the circuit monitor from the front panel to ensure that the correct meter
readings are provided. If the neutral current is also being metered, the primary rating of the current
transformer (CT) used for the neutral current would also be entered into the circuit monitor from the
The ratings for the current and voltage transformers can be found on the one-line diagrams of the
switchgear in which the circuit monitors were installed. If the circuit monitor installation was a retrofit,
then the current and voltage transformer ratings will be included with the documentation used to order
*Note: the external sync pulse input via IOM module input S1 can be enabled by setting demand
interval to zero minutes