Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
What is the response time from detecting a disturbance/transient to triggering a digital output?
Power Quality Detection
To determine the response time of a digital output from a power quality event
ION7550/7650 can do high-speed digital out triggering since the digital out module will update every half-cycle (i.e. 0.01s for 50Hz). Thus, when the transient module fires AnyTrig, the digital out module will respond within 0.01 seconds.
However, the actual amount of time from a sag/swell/transient on the line, to the digital output triggering is not a half-cycle. The half-cycle time represents the transient/sag/swell ION modules update rate. The actual chain of events is as follows:
1. Transient occurs during a sampling window (1/2 cycle)
2. DSP processes transient (1/2 cycle)
3. DSP transfers data to main processor, and main processor fires ION modules (1/2 cycle)
4. Digital out changes state (1ms for solid state digital outs, 8 to 15 ms for mechanical relays)
At 50 Hz, the total time for the solid-state digital out to change state based on a transient at the start of the sampling window, is 1.5 cycles + 1ms = 31ms.
At 60 Hz, the total time for the solid-state digital out to change state based on a transient at the start of the sampling window, is 1.5 cycles + 1ms = 26ms.
The sag/swell and transient modules can both be used to trigger digital outputs in this case, as they are both high-speed modules.
You can use a Pulse Merge Module to trigger the digital out from both at once. It is also likely you will need to use a One Shot Timer to turn the digital output off again.
Sign up for all the latest solutions, offers and best practices straight to your inbox.
We are excited that you have joined the group. You will receive your welcome email soon describing the program and what to expect in the upcoming weeks. Enjoy!