Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
1. If the meter is powered up with a dead battery or a disconnected/loose battery it will show a checkerboard pattern on the screen for several seconds.
2. All configurations applied to the meter such as PT/CT ratios, Integrator values and other framework changes will be lost.
When the battery is dead or disengaged and the it is power cycled, the meter performs a factory initialization. A factory initialization causes the meter to lose its configuration data and custom template changes.
This issue cannot be fixed in the field. If you experience this issue and are unable to utilize the workaround, please contact Schneider Electric or distributor to initiate an RMA to return the meter to the factory for battery replacement while avaliable.
Ensure the meter is not power cycled. This can be accomplished via a backup power supply such as a UPS.
Note: This behavior does not apply to the 7300 meter types but the resolution is the same.
Please note: The batteries on the 7330/7350 meter are meant to last for at least 10 years. The battery life can be checked from the front panel under Name Plate info. Option. Unfortunately the battery life percentage indicator is meaningless if the battery is already dead and the meter has been power cycled.
Sign up for all the latest solutions, offers and best practices straight to your inbox.
We are excited that you have joined the group. You will receive your welcome email soon describing the program and what to expect in the upcoming weeks. Enjoy!