Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
Yes, Some of the Momentum ENT modules have problems when trying to save their IP address to Flash. You can Identify if your ENT has this problem if the serial number of that module is in the range of 310132xxxxx to 310203xxxxx AND if you peel back a label that says REV xx on the PCB side and the chip has a you need to send that module in for an exchange. An executive has been developed to correct the problem for newly manufactured ENT's to be able to use both types of flash ram chips. If the chip inside has a symbol of then continue to use it. If your ENT does not have both of these descriptors as describe above then the IP address problem you are having is being caused by something else.
Sign up for all the latest solutions, offers and best practices straight to your inbox.
We are excited that you have joined the group. You will receive your welcome email soon describing the program and what to expect in the upcoming weeks. Enjoy!