The Internet of Things (IIoT) offers unprecedented possibilities for industries. Stay ahead with EcoStruxure™ Plant and Machine.Learn more
...with the EcoStruxure™ Facility Expert (formerly known as Facility Hero) app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
The story behind the Shedd Aquarium, a smart, sustainable facility that connects people to animals, with EcoStruxure™.Discover how
Welcome to the Schneider Electric Global Website×
Using Designer, it is possible to only log a measurement when it changes value.
The following modules are needed:
Data Recorder Module
The Arithmetic module will compare the current value of the measurement to the last value. When the different between those two values is anything other than 0, the output of the arithmetic module will be 1. The convert module will see the change from 0 to 1 and pulse out to the record input of the Data Recorder Module. The value being compared will be the source of both the Arithmetic Module and the Data Recorder Module.
Input of the Arithmetic Module
Formulas used in the Arithmetic Module
Input of the Convert Module
Input of the Data Recorder Module
Sign up for all the latest solutions, offers and best practices straight to your inbox.
We are excited that you have joined the group. You will receive your welcome email soon describing the program and what to expect in the upcoming weeks. Enjoy!