Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
Goals and Symptoms
When viewing kVAR or kW real time data from a PM800 meter in ION Setup 3.0, the user may see a larger number where it should be a much less negative value.
Causes and Fixes
The driver was programmed to read the register as an unsigned 16 bit register rather than a signed 16 bit register. This causes negative KVAR and KW values to show incorrectly.
This issue has been addressed and resolved in ION Setup 3.0.13080.01 and later. However, installing the latest build on top of an earlier build may not update the tables correctly. In that case the software will need to be either uninstalled and reinstalled or the steps below can be followed.
1. Using Explorer, go to the ION Setup program folder (typically C:\Program Files\Schneider Electric\ION Setup) and then into the Tables\SQD800 sub-folder. Next, for each of the sub-folders found in that folder, repeat steps 2 thru 4.
2. Open the REALTIME.PML file using Notepad and find the lines similar to the ones listed below:
R5C3=41140,7,7,kW Phase A
R5C4=41141,7,7,kW Phase B
R5C5=41142,7,7,kW Phase C
R6C3=41148,7,7,kVA Phase A
R6C4=41149,7,7,kVA Phase B
R6C5=41150,7,7,kVA Phase C
R7C3=41144,7,7,kVAR Phase A
R7C4=41145,7,7,kVAR Phase B
R7C5=41146,7,7,kVAR Phase C
3. Modify the first "7" entry to an "8" instead for all the above lines, so those lines now look like:
R5C3=41140,8,7,kW Phase A
R5C4=41141,8,7,kW Phase B
R5C5=41142,8,7,kW Phase C
R6C3=41148,8,7,kVA Phase A
R6C4=41149,8,7,kVA Phase B
R6C5=41150,8,7,kVA Phase C
R7C3=41144,8,7,kVAR Phase A
R7C4=41145,8,7,kVAR Phase B
R7C5=41146,8,7,kVAR Phase C
4. Save the file and reload the real-time display in ION Setup
Sign up for all the latest solutions, offers and best practices straight to your inbox.
We are excited that you have joined the group. You will receive your welcome email soon describing the program and what to expect in the upcoming weeks. Enjoy!