Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
What is the input impedance for the ION 8600 IRIG-B connection?
ION 8600 series meters
Customer would like to Synchronize their ION Meters via GPS. In such a case, it is possible to only have a limited number of devices (like ION meters and Relays) on a single clock because the impedance of too many devise in series will impact the clock signal.
Configuring the ION 8600 meters to do Time Sync.
The input impedance for the IRIG-B input on the ION8600 is 425 k ohms at 5V DC.