Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
Meters do not show the correct time and/or reset their time automatically to an incorrect time (one hour off) in SMS, ION, SPM, and/or PME.
CM2000, CM3000, CM4000, PM700, PM800, PM5000 Series Meters and PM210 Meter
Power Monitoring Software SMS, ION, SPM, and PME
PowerLogic Circuit Monitors (CM2000, CM3000, CM4000) and Power Meters (PM200, PM700, PM800, PM5000) do not take into account Daylight Savings Time (DST) on board the meter. When the data is read into software (SMS, ION, SPM), the time is adjusted.
During DST, if the local time is 2:00PM, the CM or PM will read 1:00PM on the front display.
The software will make the approrpiate time corrections on data displayed and logged, but the individual meters will reset to show the time without adjustment for daylight savings. The software time will be correct during daylight savings, but the meter will show one hour difference at the meter display.