Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
When deriving control power from either a control power transformer or a metering potential transformer where the secondary voltage is 250 Vac or less, use a standard 1 A time-delay, 250 Vac fuse. An example of a suitable fuse is the Bussmann FNM.
If the control power is derived directly from the line voltage (305 Vac or less), use a rejection type time-delay fuse rated for 600 V, 3 A such as the Bussman type FNQ-R.