Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
When using ION setup to configure the datalogs for a CM2000 series power meter, it may not send the changes made to the meter. It will instead reset or disable the datalog, or set the number of channels to zero.
CM2000 series meter
Customer wants to configure the datalog on CM2xxx series meters but it does not save changes.
Configuring the datalog on CM2xxx series meter using ION Setup tool.
*Warning: Take backups of any files (i.e. datalog files) prior to modifying them. Ensure the backups are in a location that will not be overwritten (i.e. the Desktop).
This is due to the memory in the CM2000 series meter being maxed out. Lower the number of records and/or channels to resolve this issue.
If this still doesn't resolve the issue, then try upgrading the firmware on CM2xxx meter by follwing this link: FA221408
After upgrading to the latest firmware, try configuring datalog through ION Setup.