Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
Goals and Symptoms
When a user selects "Relay Name" in the "Relay & Recipient" tab, a yellow triangle will show beside "Relay Name" and a description of a Object Error. ENM will not allow the user to proceed.
Facts and Changes
Event Notification Module 7.0
Causes and Fixes
ENM 7.0 is not compatible with IE9.
Downgrade to IE8 and make sure to use IE8 in compatibility mode.
If Internet Explorer 9 has been installed by Windows Updates, then it can be removed by going to Control Panel\Programs and Features\Installed Updates