Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
When shutting down one or several (not all) I/O servers, performance may decrease according to the length of I/O server names. The affect on performance has not been quantified, but could be noticeable.
The cause of the drop in performance is a function which compares a string (in this case, I/O server name) character by character. An I/O server name of "IOServer1" will have 9 comparisons, while a name of "IO1" will have only 3. This difference could have a noticeable affect on performance while one or several I/O servers is being shut down. There is no performance impact while I/O servers are running, so alarms, real-time data, etc. are not affected.
The recommended action is to use I/O server names that are as short as possible.
Keywords: PLSCADA, PL SCADA, PowerSCADA, Power SCADA, StruxureWare PowerSCADA Expert, SPE 7.2, 7.20
Sign up for all the latest solutions, offers and best practices straight to your inbox.
We are excited that you have joined the group. You will receive your welcome email soon describing the program and what to expect in the upcoming weeks. Enjoy!