Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
Goals and Symptoms
Customer is logging value X every Y minutes
Value X is reset back to 0 after it has been logged.
How can the user keep a running total of that value?
Facts and Changes
StruxureWare Power Monitoring (SPM) or ION Enterprise (IONE)
Causes and Fixes
A cumulative usage or totalizer is needed.
Use an arithmetic module with the following formula:
S1 + PR1
Where S1 is X
Where PR1 is the previous result from R1.
Set the CalcNow of the arithmetic module to the pulse of quantity X's reset.
Assume the following:
Data value X is reset every 15 minutes after logged.
At the end of 15 minutes X = 5
At the end of 30 minutes X = 2
At the end of 45 minutes X = 11
At the end of 60 minutes X = 7
Arithmetic Module's formula would output the following:
At the end of 15 minutes R1 = 5
At the end of 30 minutes R1 = 7
At the end of 45 minutes R1 = 18
At the end of 60 minutes R1 = 25