Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
Goals and Symptoms
The readings on the EGX web page are 10% of the actual values for the 100A BCM model.
Facts and Changes
EGX300, 100Amp BCM models
Causes and Fixes
The EGX300 firmware was initially incorrect in that it was assumed both the 50A and 100A registers maintained the same programming. This error was corrected in the EGX300 firmware 4.3 and above.
The document for the 50A version says: "Registers 1-42 represent the real-time current for each channel (circuit) expressed in milliamps (10000 = 10.000Amps)"
The document for the 100A version says this "Registers 1-42 represent the real-time current for each channel (circuit) expressed in 10s of milliamps (1000 = 10.00 Amps)"
The issue has been resolved with the release of firmware version 4.3 and above. Update the firmware in the EGX300 to 4.3 or greater to resolve the issue. The firmware now separates the BCM into two different devices, one for the 50A and one for the 100A model. You will need to select the correct model type and the real time current values will be corrected.